> >
>

# Shore Plug at house for Motorhome

#1
07-09-04, 04:18 PM
mallan4929
Visiting Guest
Posts: n/a
Shore Plug at house for Motorhome

I want to wire a shore plug for my motorhome at the house. I have a 30amp outlet today that I plan to move.

My questions is concerning the length of the run and the voltage drop due to resistance. I need to add a junction box to the existing 30 ft 10/3 wire and add another 100ft of 10/3 (which I will bury). I plan to keep my frig and one airconditioner running to keep things from spoiling. Both are 110 applicances.

I know I will get some drop in the 30 amps, but can't find a reference table that tells me how much drop. Does anyone know how I can calc the drop?

Will heating be a problem due to the length of the run and splice at the junctions box?

Advise from an electrician would be welcomed. Demand for electricans is so high, I can't get one to come out to do a small job like this!

thanks!

#2
07-09-04, 05:06 PM
Member
Join Date: Sep 2000
Location: United States
Posts: 18,497
10/3? You only need 10/2 for a 120-volt circuit. You're going to have a wire you don't know what to do with.

If you google for "voltage drop calculator", you'll get all you need to compute voltage drop.

130 feet of #10 copper running 30 amps drops 8 volts. That's too much. You'll need #8, which will only drop 5 volts.

Last edited by John Nelson; 07-09-04 at 09:15 PM. Reason: Corrected typo. 20 changed to 30.
#3
07-09-04, 07:05 PM
mallan4929
Visiting Guest
Posts: n/a
30 amp - not 20 amp

John - thanks for the response.

The outlet will be 30 amps - not 20 amps as stated on your reply. Does this decrease the voltage drop to and acceptable %?

Also - a 30 amp RV plug requires 3 wire. 1 -hot, 1 neutral, and one ground.

#4
07-09-04, 09:03 PM
Member
Join Date: Nov 2003
Location: NE INDIANA
Posts: 111
If you use 10-2 with ground, you'll have your three required connections... black for hot, white for neutral, ground wire for ground... 10-3 will have an additional red wire that you won't need, but will have paid extra for.

#5
07-09-04, 09:14 PM
Member
Join Date: Sep 2000
Location: United States
Posts: 18,497
Sorry, the 20 was a typo. Replace the 20 with a 30 and the rest of the post is as I intended it. I think I'll go back and edit that 20 to a 30 so you can see what I meant. So you still need #8 for acceptable voltage drop, and even that is marginal. 130 feet is a long way to run 120-volt power

I guess the 10/2 vs. 10/3 thing was just terminology. Assuming you are using NM-B and/or UF-B, 10/2 is the name of the cable with black, white and ground.

Posting Rules
You may not post new threads
You may not post replies
You may not post attachments
You may not edit your posts

BB code is On
Smilies are On
[IMG] code is On
HTML code is Off