> >
>

# How to connect two 3-way switches at opposing ends of a hallway

## How to connect two 3-way switches at opposing ends of a hallway

#1
01-15-14, 07:11 PM
Member
Join Date: Mar 2012
Location: USA
Posts: 327
How to connect two 3-way switches at opposing ends of a hallway

Does there need to be separate power sources to both ends of hallway for two 3-way switches?

Switch A:
12-2 Romex electrical cable from circuit breaker 5
12-3 Romex electrical cable to switch B

Switch B:
12-2 Romex electrical cable from circuit breaker 5 via junction box
12-3 Romex electrical cable from switch A
12-2 Romex electrical cable to lights

My question is, do I need to have the 12-2 electrical cable in switch B?

#2
01-15-14, 07:19 PM
Member
Join Date: Mar 2006
Location: USA
Posts: 29,711
No. The hot black at A connects to common. The black from the light at B connects to the common there. There is no need for a power in at 2. Power from A to B is carried by the two travelers.

#3
01-15-14, 09:31 PM
Member
Join Date: Oct 2013
Location: United States
Posts: 189
3-way switches

Here are a couple drawings for 3-way switching.

#4
01-20-14, 07:49 PM
Member
Join Date: Mar 2012
Location: USA
Posts: 327
Thanks guys. I'm just going to make things simpler and do it right with how Ray is saying. Since the power for my 2nd switch (i.e., switch B) has power coming from the 12-3 electrical cable travelers, then I am just going to remove the 12-2 electrical cable going into that switch.

#5
01-20-14, 07:56 PM
Forum Topic Moderator
Join Date: Jul 2002
Location: Maryland
Posts: 13,978
You cannot power another switch from the travelers of the other switch.

#6
01-23-14, 12:22 AM
Member
Join Date: Mar 2012
Location: USA
Posts: 327
But pcboss, Ray is saying that you can power a switch (i.e., switch B) from the travelers of another switch (i.e., switch A).

#7
01-23-14, 05:18 AM
Member
Join Date: Mar 2006
Location: USA
Posts: 29,711
Switch B is part of the same circuit. PCboss means a switch on a second circuit.

#8
01-26-14, 06:51 AM
Member
Join Date: Mar 2012
Location: USA
Posts: 327
I really don't understand what pcboss is saying. So, am I ok to just remove the 12-2 Romex electrical cable from switch B as written in my original post?

#9
01-26-14, 09:20 PM
Member
Join Date: Mar 2012
Location: USA
Posts: 7,458
Originally Posted by pcboss
You cannot power another switch from the travelers of the other switch.
I really don't understand what pcboss is saying.
PCboss is saying that an additional switch for an an additional set of lights cannot be fed from the wiring coming to Switch B from Switch A. That's true, but that's not what you're trying to do so you don't need to worry about it.

So, am I ok to just remove the 12-2 Romex electrical cable from switch B as written in my original post?
In your original post you wrote:
Switch B:
12-2 Romex electrical cable from circuit breaker 5 via junction box
12-3 Romex electrical cable from switch A
12-2 Romex electrical cable to lights
It's not only OK, it's good practice to remove the power feed from the panel from the box for Switch B. You have a panel feed to the box for Switch A and you don't need a second one.

You will need the cable going to the lights.