> >
>

# 4 gang fill capacity

#1
03-04-02, 08:06 AM
Roman
Visiting Guest
Posts: n/a
4 gang fill capacity

I have a 4-gang Carlon new work box that will house four 3-way switches. The box volume as inscribed on the box is 60 cu. in. and has a wire fill capacity of 26 12 AWG wires. I have four 12/3 and three 12/2 romex cables in the box and I believe I am exceeding the wire fill capacity of the box and would like some suggestions on how to avoid this problem.

Three of the 12/3 cables go to a 3 gang box at the other end of the room that contains the three other 3-way switches. Cables carrying power to the light fixtures for all three switches come out of the other 3 gang box (which has a wire fill capacity issue as well). The other 12/3 wire goes to a different box. One 12/2 wire is power in, the second is power out to other devices, and the third is power to one of the fixtures being controlled by one of the 3-way switches.

My wire fill calcs:
12 (three conductors for each of the four 12/3 cables)
6 (two conductors for each of the three 12/2 cables)
1 (ground for all)
1 (cable clamp for all)
8 (two conductors for each of the four 3-way switches)
-----------
28 total conductors x 2.25 = 63 cu. in. (which is over the capacity of the box)

Are my calcs correct? Does anyone have any suggestions on how to reduce the number of conductors? Since three of the 12/3 cables lead to the same box on the other end and since the neutral for all three will be connected together, can I run one 12/3 and two 12/2 cables instead of three 12/3 cables to the other three 3-way switches? Are there extension rings available that increase the volume of 3 and 4 gang boxes?

Thanks.

#2
03-04-02, 04:52 PM
Member
Join Date: Feb 2002
Location: port chester n y
Posts: 2,117
I suggest using a"deep" metal gem box which can be "made" into any number of gangs.You'll avoid 4 grounding leads to the switches.Also try to re-arrange the wiring so each gang,or switch,has a 12/3 and 12/2 "standard" connection.The 12/2 (at each switch or gang) goes to the controlled fixture.The 12/3 is from the "first" 3-way and has 2 "pivots" (Red & Black) and the neutral (White). The 2 Whites splice together and the Black of the 12/2 and the Red & Black of the 12/3 terminate on the switch.A 4-gang box with 4 3-ways can get complicated !! Good Luck!

Posting Rules
You may not post new threads
You may not post replies
You may not post attachments
You may not edit your posts

BB code is On
Smilies are On
[IMG] code is On
HTML code is Off
Pingbacks are Off
Refbacks are Off