Hot Topics: Why Is There Goo Behind This Breaker? Hot Topics: Why Is There Goo Behind This Breaker?
Here at DoItYourself.com we enjoy providing a place where home improvement novices and experts can come together to share ideas and advice. Inside our Forums, users can browse threads to see what exchanges are taking place on a topic of interest or start their own dialogue by posting something for the community to take part in. With over 250,000 members and counting, this resource is quite active so each week we highlight one of the conversations that may just help you with that next DIY project.
Get all your ducks in a row for some electrical DIY, and then find out that the original electrician did something you weren’t expecting. What’s this stuff he used? Does he know more than you? Maybe you’ve skipped a step for years without knowing it – or maybe not. The Forum identifies the substance.
Original Post: Breaker goop?
As I'm replacing/moving some breakers, I noticed on the back of the original ones there's this charcoal-colored goop on the contact area. Is this supposed to be there?
Highlights from the Thread
pcboss Forum Topic Moderator
That looks like the breaker has taken too much heat and melted. Compare that to a new breaker to see how it should look.
It's not melted plastic. It's like a grease.
PJmax Group Moderator
Some electricians apply Penetrox, which is an anti-corrosion grease, to aluminum bus bars in panels. Although not required and is not detrimental to the performance of the breaker... that is way too much on those breakers. There should only be a very thin film.
If you intend to clean the bus bars, be sure to turn off the main before touching them. Wouldn't hurt to check them with a meter to confirm they are dead.
I also think that is anti-oxidant grease and it should have never been used. Anti-oxidant is used to protect aluminum wire connections from oxidizing. The aluminum bus bars in a load center/panel board are tin plated, the anti-oxidant does nothing except make a huge friggen mess.
Hahaha. OK, thanks.